Power systems for transmission SS
For reliable operation of protection devices, monitoring and control of the substations quality uninterruptible DC voltage is necessary. It can only be ensured by power supply system which is appropriately and precisely designed, professionally manufactured, competently tested and professionally implemented in the facility. For the manufacturing of such supply systems KONČAR uses only the highest quality components of renowned manufacturers (battery, special circuit breakers for DC distribution etc.). The numerous positive references from different power facilities confirm the soundness of the approach and practices.
The most important energy facilities (thermal and hydro power plants, large transmission substations, etc.) should have the highest possible reliability of power supply because the possible damage caused by a power supply failure at a critical moment can surpass by far the price of power supply.
The right choice for such facilities is redundant parallel connection of two completely independent power supplies. Thereby independent double supply of each load or a small group of loads is provided. Redundancy of cables themselves is often applied. High reliability is based on the requirement that the failure of one system does not in any way affect the operation of other system, which continues to supply all loads without interruption.
This is avoided by use of large cross-section conductors which makes it more expensive. Furthermore, in these facilities the power supply distribution system often must comprise four levels of selectivity, which is more complex to design and it adds to costs.
The optimal solution for such large facilities is the installation of a distributed power supply system. Instead of one central power supply system for all load equipment, each equipment group has their own power supply system.
For the smallest plants, with a small number of end loads, DC voltage distribution bord is designed with selectivity in two levels. In most other plants DC voltage distribution bord is designed with selectivity in three levels. There are very large plants with several hundred meters long cables by which the equipment is connected to the power supply. In their case the selectivity in three levels is unsatisfactory solution so DC voltage distribution bord is designed with selectivity in four levels.
It is necessary to carefully design DC voltage distribution bords in order for the selectivity to be ensured in all border situations. This is especially true for the most complex systems with DC distribution bords where it is necessary to achieve selectivity in four levels. Such configurations represent a real design challenge as only a very few circuit breakers are eligible for such applications, and the distribution bord itself inevitably has increased price.
In such cases it is necessary to examine the actual state of power supply and implement appropriate reconstruction. Often it is necessary to redo the design and reconstruct a complete power supply system. It is a very delicate task, which requires a high skill and experience. KONČAR successfully reconstructed many substations, but because of the scope and complexity of the activities, the most important references are impeccable reconstruction of the largest hydro power plants and thermal power plants in Croatia.